Today the Pole Barn Guru answers reader questions about floor plans, adding spray foam to an existing structure for condensation control, and solutions for a sill at 18′ OHD opening.
DEAR POLE BARN GURU: What do you charge to take my floor plan and send me engineered drawings? SHANNON in JONESBOROUGH
DEAR SHANNON: We only furnish engineer sealed plans and verifying calculations with your investment in a new Hansen Pole Building. If you just need professionally done floor plans, please check this out: http://www.hansenpolebuildings.com/post-frame-floor-plans/?fbclid=IwAR2ta5IFSxrltv5eAyBVmg-JUsoPfy9hbWtP86svOTPfG1q5pGmfhA7yd5Q
DEAR POLE BARN GURU: Hello! I have recently purchased a pole building that is not insulated & It does not have the vapor barrier/plastic installed between the wood framing and the sheet metal. We would like to insulate this building. We are thinking spray foam because I have heard you can apply it directly to the steel. Do we have any other options for insulating this? Any advice is greatly appreciated. Thank you!! KRYSTA in SPOKANE
DEAR KRYSTA: If it has no sort of condensation control between roof framing and roof steel then two inches of closed cell should be sprayed to underside of roof steel to control condensation. If your roof trusses are designed to support a ceiling, then install one and blow in R-60 fiberglass on top of it, ventilating the dead attic space appropriately.
For your walls, you can use rock wool insulation batts, completely filling wall cavity, with a well-sealed vapor barrier on interior face.
DEAR POLE BARN GURU: I need to pour a concrete sill at the 18’ wide entry to my pole shed in South central Wisconsin. The interior of shed is compacted crushed limestone, the apron leading up to it will be asphalt so a concrete sill seems like a good idea to protect asphalt edge. I can’t find any advice online so I hope you can help me out with your expert thoughts. First, good idea? Second, thickness. It would be about 12” wide. The base is 30 years old, thick and well compacted. Any help would be greatly appreciated. Thanks for your time. JAPH in WISCONSIN
DEAR JAPH: My concern would be possible frost heave of a concrete sill. I would probably excavate outside my building so top of asphalt and top of interior compacted crushed limestone were at same grade and call it good. Takes away possible heave of concrete and saves cost of concrete.
Looking for a three bedroom; one master suit with bathroom, two separate bathrooms, two and a half garage stalls, kitchen, living room and dinning room open concept. Laundry room in the entrance area from the house to garage.
Thank you for your interest, one of our Floor Plans Specialists will be reaching out to you shortly, or call 1.866.200.9657 for immediate assistance.